On a recent service call it was discovered that a fresh air damper was stuck open. The damper actuator was receiving 2VDC but no action. The damper spring returns with zero issues. This repair of replacing the the actuator and outdoor enthalpy switch should solve the issue.
Save 8% on your purchase https://www.trutechtools.com/ with promo code knowitall
Check out https://www.hirago.com/
Visit HVAC Know It All on social media Facebook https://www.facebook.com/hvacknowitall/
Instagram https://www.instagram.com/hvacknowitall/ LinkedIn https://www.linkedin.com/in/gary-mccr…
Listen to the HVAC Know It All Podcast https://www.linkedin.com/in/gary-mccr…
Visit https://www.hvacknowitall.com/ for articles, and tips.